The sections show below are commonly used and type tested assemblies, but the flexibility of our System 50 design means there are many more variations and configurations available.
Cabling and maintenance access is from the rear of the switchboard with a minimum recommended access of 1m. Cable entry is through the bottom of the switchboard cubicles. Section height is 2250mm. Section depth is 800mm. Sections are fitted with 4 off, removable lifting eye bolts for delivery.
You can also download this document in pdf form.
Side view, rear access switchboard
Incoming sections in combinations of 600 wide. Maximum incoming rating 1600A
Double stack of outgoing switches. Maximum total outgoing rating 1400A. Maximum outgoing switch rating 200A
Two outgoing 400A switches
Single stack of outgoing switches. Maximum total outgoing rating 1400A. Maximum outgoing switch rating 200A.
Combined outgoing section. Upper switches <200A. Lower switch <800A.
Combined outgoing section. Upper switches <200A. Lower switch <400A.
Any weights specified are for guidance purposes only. Actual section weight is dependant on final section contents.